Manuals for buderus juno c to download for viewing them online or printout as PDF. Manuals for Buderus Juno 11 download to download for viewing them online or printout as PDF. Buderus Manuals for Support Juno /SF Buderus | GB | Operating instructions | Buderus GB Operating instructions . .. 46 Shut down the heating system using the control unit.
|Published (Last):||9 April 2005|
|PDF File Size:||1.76 Mb|
|ePub File Size:||16.45 Mb|
|Price:||Free* [*Free Regsitration Required]|
It is not essential for the boiler to be positioned this way. Reduce the system pressure to achieve the initial cold fill pressure.
If, for example, you want to reduce the room temperature buderrus the reference room, and you therefore close the thermostatic valve further, the flow rate through the radiator is reduced and, therefore, less heat is transferred to the room. P Loose contact or defective safety sensor. On all weekdays DHW should be heated from Textplatte Logamax Plus GB Suitable for new installations and for replacing existing sealed system Boilers. Factory-set permanent display, if the MEC2 is fitted in the control unit.
Download – Buderus –
The operating mode determines the switching state: Immediately call a D. Press the reset button once the temperature has dropped sufficiently. Check the operation and safety of the air intake and flue pipe 32 Is the mains electricity supply switched on? The heating system will only become operational again if the pressure is nuno to The Boiler and storage tank each have a drain to facilitate this.
A single switching point comprises three details: If the switches are not set to automatic, a corresponding message appears on the MEC2 programming unit, and illuminates. Is the size of the pipe adequate for the boiler rating? Burner starts but will not light up This can be due either to absence of oil ignition. FM — heating circuit 3, heating circuit 4 Logamatic – Subject to technical modifications. Otherwise a fault message “Setting Not possible.
Bottom of oil tank below Raise tank or install a two pipe oil supply from level of oil pump tank. Flue measuring points pos. It starts the heat source boiler and burner and pumps when warm rooms or DHW are required.
High level side outlet balanced flue RH or LH. This appliance is equipped with an buddrus device which automatically lights the burner. Including near the floor.
Operating instructions Logamatic 4211
From within the roof space if space permits: Secure any vertical lengths by using a drill and 4 self tapping screws supplied. Hand over the technical documents. Compliance with the Building Regulations does not indicate that the chimney is satisfactory in respect of draught conditions, or is positioned so that down draughts will not occur.
To adjust the CO2 at the Air Shutter use a 3mm allen key as shown. Before you utilise this option, buderuss the following: With the seals fitted slide the extension into the offtake socket external seals end first. Refit parts and inspect seals etc. Next switching point Continue to turn the rotary selector until the next switching point is displayed. Setting the operating mode for DHW circulation.
Burerus heating phase has been deleted when no blocks are left.
Allow system to cool, check pressure in system and Air trapped in boiler heat repressurise if required. Use or to select Day. Summer mode is indicated on the display with symbol. Clear oil filters and de-sludge the tank if necessary. At the same time, the temperature in all rooms without thermostatic valves increases due to the higher boiler water temperature.
Wiring should not be tampered with, modified or changed for any reason. The temperature is set on the thermostat e.
Logamax plus GB str. You can recognise the currently enabled heating mode because the green LED illuminates.
It may also be employed to exhaust vertically to avoid nearby windows or doors.